|Place of Origin:||HENAN, CHINA|
|Minimum Order Quantity:||1set|
|Packaging Details:||Nude packing,Package with Steel Box,or Wooden Box|
|Payment Terms:||T/T, L/C, Western Union|
|Efficiency:||82.56%||Color:||Gray, Golden, Orange, Blue|
|Fuel:||Biomass/Wood Pellet/Wood Chip/Rice Husk||Water Circulation:||Natural Circulation|
|Application:||Industrial||Burner:||Riello, Baltur,or Optional|
|Installation:||Assembled Boiler||Media:||Steam And Water|
Customized Rice Husk and Wood Chip Biomass Fired Steam Boiler with Long Service Life
- Biomass boiler is based on the technology of the original layer burner, applying the company's core technology, overcomes the high temperature spinning flow field in the furnace, completely solves the problems of combustion coking and black smoke in the presence of biomass particles, boiler thermal efficiency.
- From coal-fired boilers increased by 78% to 85% to 90%. Biomass fuels are very diverse and have regenerative, recyclable properties, including crop straw, wood chips, sawdust, peanut shells, corn cobs, rice husks, branches, leaves, hay, etc., or shaped fuels.
- The calorific value is 3600~5100 kcal/kg, which can completely replace coal and other fuels, and its price is low, and the operating cost of the boiler is greatly reduced.
- As the fourth largest energy source other than coal, oil and natural gas, biomass fuel is environmentally friendly and environmentally friendly. It has also been recognized and promoted by users in the market.
2, The comparsion and analysis of common fuels based on 1 ton steam boiler is list below.
According to the paraments in the table, it is obviously that overall performance of sawdust, straw, rice husk and biomass fuel is very high. So the biomass steam boiler is a nice choice for your factory.
|Calorific value,Cost,Cost Analysis and Comparison of Various Common Fuels
(Based On 1 Ton Steam Boiler)
|Fuel||ⅡSoft Coal||Light Oil||Natural Gas||Sawdust||Rice Husk||Straw||Biomass Forming Granule|
|Fuel density (kg/m3)||1200||850||0.741||130||120||80-100
|Low calorific value (KJ/kg)||17693||42875||35590||13101||12689||16697
|Boiler thermal efficiency (%)||80||95||96||88||87||90||90|
|Market price (¥/ton)||600||7000||3.4||300||550||300||800|
|Fuel consumption (kg/h)||200||66.1||79.4||180||200||160||160|
3, Product technical features:
1. According to the type of fuel given, the current internationally leading biomass fuel feeding technology is used.
Due to its low calorific value and low density, biofuels make the feeding system a key technology for bio-based direct-fired boilers. The feeding system introduced by YONGXING Company is highly automated, easy to use and has good reliability. In the conveying system, there is a fireproof, explosion-proof, anti-self-ignition, anti-blocking system, and a fire water device is provided, which has high safety.
2. The combustion system consists of a water-cooled vibrating grate plus a graded air supply system.
The water-cooled vibration grate designed for burning biomass fuel periodically vibrates when the fuel is burned, which not only ensures the full combustion of the fuel, but also controls the residence time of the fuel, so that the water-cooled grate is less prone to slagging. The grate drive unit adopts a full set of imported equipment and frequency conversion control. Has many years of operating experience, high reliability and long service life.
According to the different stages of fuel combustion, the graded air supply can control the air volume at each level, which can achieve good combustion effect, prevent the occurrence of coke corrosion of the furnace, and effectively discharge lower pollutants.
3.Take effective measures to prevent high temperature corrosion and low temperature corrosion.
Biomass fuels contain high levels of chloride ions, and ash contains a large amount of alkali metals, which can easily cause corrosion on the heated surface. The company has taken a lot of measures to prevent corrosion during boiler design. At the same time, the heated surface adopts high-grade corrosion-resistant materials.
For example, high-temperature three-stage and four-stage superheater materials are all made of stainless steel SA-213TP347H, and air preheater materials are used. JNS is resistant to sulfuric acid dew point corrosion steel
4. The boiler adopts a bottom support structure with an expansion center
Most of the weight of the boiler body is transferred to the bottom support through the waterwall and downcomer and to the foundation portion of the boiler on the ground. The setting of the expansion center plays a major role in ensuring reliable operation of the boiler and good sealing.
4,The installed photo of biomass steam boiler is list below
5,The technical data of more type is as follows
|Quckly installed boiler|
|rated steam temeperature||℃||170/184||170/184||184/193/204||193/204|
|feed water temperature||℃||20||20||20||105|
|valid grate area||㎡||1.852||3.15||5.18||8.395|
|exhaust gas temperature||℃||152/160||152/161||163/163.8/169.5||163/169|
|max part size for delivery||mm||5488*2254*2782||5694*2704*3324||6743*2954*3508||8244*2951*3704|
|TWO PART ASSEMBLED BOILER|
|rated steam temeperature||℃||193/204||193/204||193/204||193/204||193/204||193/204||193/204|
|feed water temperature||℃||105||105||105||105||105||105||105|
|valid grate area||m2||7.55||9.34||10.98||12.78||16.24||20.84||24.76|
|exhaust gas temperature||℃||165.78/169.85||161/165||160/162||158/150||156.7/159.4||153/159||152/156|
|max part size for delivery||mm||7100*2800*3500
Wecome to inquire our products.
Contact Person: Bettysun