|Place of Origin:||HENAN PROVINCE|
|Minimum Order Quantity:||1set|
|Packaging Details:||Nude packing+wooden box+steel box ,and etc.|
|Payment Terms:||T/T,L/C,Western Union|
|FUEL:||Light Oil, Diesel Oil, Kerosene Oil, Heavy Oil||PRESSURE:||10bar,12.5bar,16bar|
|Boiler Capacity:||2TPH||Burner Model:||L8Z|
|Boiler Heating Area:||69.4||Flue Gas Temperature:||165|
|With Condenser Flue Gas Temperature:||＜80℃||Name:||Oil Hot Water Boiler|
oil powered boiler,
fuel oil boiler
10 Bar Gas Fired Hot Water Boiler Oil steam Boiler Heating System
WNS2-1.25-YQ oil-fired steam boiler technical data sheet
|Rated steam pressure MPa||1.25|
|Rated steam temperature °C||194|
|Feed water temperature °C||20|
|Heat transfer area m2||75.9|
|Design thermal efficiency%||91-94|
|Testing thermal efficiency||≥90|
|Water test pressure MPa||1.65|
|Boiler net weight T||7.09|
|Water capacity KG||4200|
|Air consumption (natural gas)||120Nm3/h|
|Air consumption (city gas)||300Nm3/h|
|Shipping size (length X width x height) m||4.2x2.2x2.4|
|Steam interface PN||1.6Mpa|
|Steam interface DN||80mm|
|Air supply port (natural gas) mm||DN65|
|Air supply port (city gas) mm||DN65|
|Sewage outlet DN||50mm|
|Safety valve PN||1.6Mpa|
|Nominal diameter DN (mm)||2x40|
|Natural gas (pressure) mmH20||600|
|City gas (pressure) mmH20||1000|
Our company will guide the installation and testing of the boilers sold by one or two engineers according to customer needs. The installation cycle has a small capacity boiler for 7-15 days and a large capacity boiler for 15-20 days.
During the period, the customer is responsible for the engineer's visa, airfare, accommodation, food, and salary of $80/day/person.
Main process of boiler installation China for reference
1. Before the boiler put into use or within 30 days after put into use, the unit for the use of special equipment shall register with the special equipment safety supervision and administration department of the municipality directly under the central government or the city where the district is located. The registration mark should be placed or attached to a prominent location on the special equipment.
2. After the completion of the installation, transformation and maintenance of the boiler, the construction unit that installs, renovates or repairs shall hand over the relevant technical data to the user within 30 days after acceptance.
3. The construction unit that installs, renovates and repairs the boiler shall inform the municipal special equipment safety supervision and management department of the municipality or the district where the project is to be carried out before the construction.
4. The production license system shall be implemented for the design, manufacture, installation, modification, inspection, and testing of boilers.
5. The location of the boiler should be at the lower air outlet of the plant with the most wind direction in the year.
6. Steam boiler products must be accompanied by technical information related to safety when they leave the factory. The contents should include:
1. Boiler drawings (including general drawings, installation drawings, and main pressure-receiving parts drawings);
2. The strength calculation book or calculation result in a summary table of the pressure component;
3. A summary of the calculation book or calculation results of the safety valve emissions;
4. Boiler quality certificate (including factory certificate, metal material certificate, welding quality certificate, and hydraulic test certificate);
5. Boiler installation instructions and instructions for use;
6. Major design change data for pressure components.
Boiler applicable industries: hot spring bath, sauna steam room, printing and dyeing textile, factory office school, medical and pharmaceutical, hotel catering, food processing, chemical plant, socks factory heat setting, garment processing, industrial steam washing, farm heating and drying, etc.
Contact Person: Ms. Bettysun