|Place of Origin:||HENAN, CHINA|
|Minimum Order Quantity:||1set|
|Packaging Details:||Nude packing,Package with Steel Box,or Wooden Box|
|Payment Terms:||T/T, L/C, Western Union|
|Fuel:||Coal, Wood Pellet, Biomass||Material:||Special Steel|
|Application:||Industrial||Burner:||Riello, Baltur,or Optional|
|Color:||Customer's Requirement||Structure:||Water And Fire Tube|
coal fired hot water boiler,
wood burning steam boiler
1-4 ton capacity DZH biomass and wood pellets fired steam boiler for sale with low biomass fuel cost
The DZH biomass boiler produced by the company is a horizontal three-return tubular boiler. The combustion process of the fuel can be briefly described as: the operator can throw the biomass fuel into the furnace, and after the fuel is fully burned in the furnace, the high-temperature smoke enters the front smoke box through two sets of airfoil flues arranged on both sides of the furnace. The threaded tube inserted into the drum is then inserted into the rear smoke box. It is then drawn into the flue, dust collector and chimney by an induced draft fan and finally discharged to the atmosphere. The boiler is safe and stable in operation, easy to operate, and low in failure rate.
The DZH biomass steam boiler produced by the company has the advantages of maturity, advancement, stability, reliability and economy.
1. Maturity: Our company is one of the earliest manufacturers of material-producing threaded tube boilers in China. Over the past 30 years, the products have been updated many times and become more mature. Thousands of similar products have been produced.
2. Advanced: It adopts a number of advanced technologies, such as threaded tubes, in-furnace intensified combustion, etc. The control system can adjust independently for the following situations, such as automatic adjustment of steam pressure, self-controlled water supply, high steam pressure protection, and inside the pot. Water shortage protection, abnormal water level alarm, low water level interlock protection, motor overload protection and automatic power failure protection.
3. Stability: The boiler runs smoothly, the failure rate is low, and no major safety accidents occur; the longest running time of the early boiler has reached more than 20 years.
4. Reliability: The only boiler manufacturer in China that has conducted 200,000 fatigue tests on shell boilers.
5. Economical: high thermal efficiency, fuel saving and good economy.
The details photo of biomass steam fired boiler is list below.
Description ------- Check items before the start of biomass boiler
1, Check all valves and put them in the following states:
Steam system: The main valve is closed after the switch test, and the door and other doors are closed (before the 72-hour trial run).
Water supply system: the water supply outlet and the discharge outlet are closed, and the water gate and economizer entrance door are opened.
Cooling system: After the manual door of the desuperheater is opened, the electric adjustment door is closed.
Water discharge system: the sewage door and the sewage discharge secondary door of each header are closed, the main sewage door is regularly drained, and the continuous sewage door is opened.
Drainage system: all the hydrophobic doors in front of the main valve and the hydrophobic door behind the main valve are opened.
Steam and furnace water sampling door, the drum filling door is opened, and the dosing pump outlet door is closed.
The valve and water gate of the drum water level gauge are opened and the water release door is closed.
All pressure gauges are turned on and all flow meters are turned on.
The air door is opened (the water supply air door can be closed), and the air exhaust valve is opened.
2, Check all damper flaps and place them in the following positions.
The inlet baffle of the induced draft fan is closed after the switch test, and the outlet baffle is opened.
The blower inlet baffle is closed after the switch test.
The ash removal system is in an operational state and is closed before starting.
3, Check the combustion chamber, the inside of the grate without coke and debris: the entrance, the inspection door is complete, the closure is tight, the ash discharge is smooth, and the cover is complete.
4, Check the dust collector and it is in good working condition.
5, Check the rotating machinery, the bearing lubricating oil is clean, the oil level is normal, the cooling water is turned on. The door is normal, the water flow is normal, the anchor bolt and the safety cover are firm.
6, The ignition operating system and alarm system are in good working condition.
7,The slag remover is in good working condition.
The more details table about the biomass steam boiler is below:
|DZH Biomass Steam Fired Boiler Technical Parameters|
|Model||Rated evaporation capacity t/h||Rated working pressure MPa||Rated steam temperature ℃||Body Heated area m2||Chain Grate area m2||Dimension
|Quckly installed boiler|
|rated steam temeperature||℃||170/184||170/184||184/193/204||193/204|
|feed water temperature||℃||20||20||20||105|
|valid grate area||㎡||1.852||3.15||5.18||8.395|
|exhaust gas temperature||℃||152/160||152/161||163/163.8/169.5||163/169|
|max part size for delivery||mm||5488*2254*2782||5694*2704*3324||6743*2954*3508||8244*2951*3704|
|TWO PART ASSEMBLED BOILER|
|rated steam temeperature||℃||193/204||193/204||193/204||193/204||193/204||193/204||193/204|
|feed water temperature||℃||105||105||105||105||105||105||105|
|valid grate area||m2||7.55||9.34||10.98||12.78||16.24||20.84||24.76|
|exhaust gas temperature||℃||165.78/169.85||161/165||160/162||158/150||156.7/159.4||153/159||152/156|
|max part size for delivery||mm||7100*2800*3500
1.The boiler assembly shall be in accordance with ,2000 edition and JB/ t7985-2002, .
2.The boiler is designed according to normal pressure. The top of the furnace body is provided with an air outlet.
3.The boiler runs without pressure and the combustion operation is safe and reliable.
4. Atmospheric hot water boilers can be installed in any place where they are used, and are not subject to a wide range of annual inspection procedures, and have been rapidly developed in recent years.
Wecome to inquire our products.
Contact Person: Ms. Bettysun