|Place of Origin:||HENAN PROVINCE|
|Minimum Order Quantity:||1set|
|Packaging Details:||Nude packing+wooden box+steel box ,and etc.|
|Payment Terms:||T/T,L/C,Western Union|
|Fuel:||NATURAL GAS/LPG/CITY GAS ,ETC||Pressure:||10bar,12.5bar,16bar|
|Capacity:||10t,15t,20t,25t||Circulation:||3return Or 4 Return|
|Name:||Natural Gas Fired Boiler||Save Energy:||Condensing Type|
|Structure:||Fire And Water Tube||Efficiency:||＞96%|
natural gas steam boiler,
industrial gas fired boilers
Factory directly supply large capacity gas and oil steam boiler used for textile industry
1. SZS natural gas steam boiler adopts the wet-back structure, with full flange butt welding seam, high reliability and low maintenance cost.
2. SZS boiler adopts the design of vertical d-type layout of double cassettes. The pressure of the boiler body is in good stress condition. The important pressure elements such as cassettes are not directly exposed to the radiation and erosion of high temperature flame.
3. SZS natural gas steam boiler adopts advanced corrugated furnace bladder structure, which not only increases the heat transfer area, but also satisfies the free expansion of the furnace bladder after heating.
4. The company has a professional after-sales and technical team, we will provide full service for users, and answer the technical and installation problems of steam boilers, auxiliary boilers and other products for you.
5. SZS steam boiler produced by the company adopts a large volume combustion chamber compared with the traditional boiler, which can burn fuel more efficiently and greatly improve the boiler's thermal efficiency.
6. SZS steam boiler, with its advantages of high thermal efficiency, fuel saving and pollution-free, can be widely used in food, chemical, pharmaceutical, building materials, clothing, washing, civil heating and other fields.
|Typical SZS series steam boiler technical parameter list|
|Rated evaporation t/h||10||15||20||25||35||45|
|Rated steam pressure MPa||1.6|
|Rated steam temperature °C||204|
|Feed water temperature °C||105|
|Boiler design thermal efficiency%||93.5%~100.6%|
|Common fuel||Natural gas / light diesel|
|Combustion method||Forced ventilation, micro-positive pressure combustion|
|Exhaust gas temperature °C||55~150|
|Fuel consumption (natural gas) Nm3/h||703||1055||1406||1758||2461||3164|
|Gas supply pressure (natural gas) mbar||20~30||30~50||30~50||30~50||50||50~200|
|Maximum transport weight t||27||32||37||42||51||35|
|Maximum transport size m||6.7x3.2x3.5||7.2x3.4x3.4||7.7x3.6x3.9||8.5x3.8x4.1||9.6x4.1x4.3||10.0x3.5x3.8|
|Mainframe dimensions (including platform, energy saver)||9.0x5.6x4.4||9.9x5.6x4.0||10.5x5.7x4.6||11.3x6.0x4.8||12.4x6.6x5.0||13.0x6.8x5.2|
|1. The boiler is mainly designed with natural gas and light diesel oil. It is also suitable for city gas, liquefied petroleum gas, biogas, coke oven gas and mine gas.|
|2. The fuel consumption is calculated based on the calorific value of natural gas 36006KJ/Nm3 and the calorific value of light oil 42705KJ/kg.|
|3. We follow the principle of continuous improvement and improvement of product performance. The data of the new generation products may be changed. The data in the table is for reference only.|
Installation instructions of SZS oil-gas-steam boiler -- combustion system
1. Oil and gas, the user in accordance with the design of the boiler room installation.
2. After the installation of the gas system, the water pressure test at 1.25 times the working pressure shall be carried out (the minimum test pressure shall not be less than 0.4mpa).
3. Clean water or steam cleaning shall be carried out after installation of gas system pipelines. Approved technical measures shall be taken during the washing process.
4. Oil cycle test of the whole system shall be carried out after installation of the gas system.
5. The gas should be sent to the burner in the shortest distance, and the diameter of the air supply pipe must be a certain value larger than the accessories pipe of the burner.
6. Gas pipe installation should be done after the air tightness test, the test in advance without accessories section in the air or inert gas is greater than 0.1 MPa, the total test includes from the main cutting device on the burnerblock valves of all equipment, pipeline under the condition of the solenoid valve closed with air or 7. Times the working pressure of the inert gas, but the pressure is higher than at least 5000pa, joint with foam material or the material does not cause corrosion coating.
Contact Person: Ms. Bettysun