WNS 15 t / h Best Service and Technical Support Industrial Gas Fired Steam Boiler
This product model is WNS15-1.25-Y(Q) ,LPG gas fired steam boilers Main Technical datasheet :
Boiler model: WNS15-1.25-YQ
Rated evaporation: 15t/h
Rated steam pressure: 1.25MPa
Rated steam temperature: 194°
Suitable for fuel: natural gas, gas, liquefied gas, etc.
Rated air consumption: 1050m3/h
Thermal efficiency: 95%
The design of this product complies with the provisions of TSG G0001-2012 "Boiler Safety Technical Supervision Regulations" and TSG G0002-2010 "Boiler Energy Saving Technology Supervision and Management Regulations".
1. The fuel gas steam boiler is an internal combustion three-return fire tube boiler.
2. The low-position symmetric arrangement of the furnace bile wet-back structure, the high-temperature flue gas flushes the second and third return smoke pipes in turn, and then the rear smoke chamber is discharged into the atmosphere through the chimney.
3. The boiler is equipped with movable front and rear smoke box covers to facilitate boiler maintenance.
4. The boiler is equipped with a high-tech industrial burner.
It adopts automatic regulation of combustion, automatic adjustment of water supply, program start-stop, fully automatic operation and other advanced technologies, and has automatic protection functions such as high and low water level alarm and extremely low water level, ultra high steam pressure and flameout.
5. Fuel gas steam boiler The boiler has compact structure, safety and reliability, easy operation, quick installation, less pollution and low noise.
1. There is a door on the rear of the fuel or gas boiler or on the pipe. The door position should be favorable for venting. Where the explosive gas may endanger the safety of the operator, a pressure relief guide tube shall be installed on the door. Fuel gas steam boiler
2. The installation of the boiler and its auxiliary equipment, water treatment equipment, etc. shall comply with the technical requirements of the equipment manufacturer. The equipment foundation must be constructed only after the equipment arrives and is checked against the design drawings.
3. When installing the equipment, avoid placing equipment and installation materials on the floor. When using building columns and beam lifting equipment, the bearing capacity of beams and columns must be verified in advance.
4. The pressure test acceptance after installation of fuel, gas, hot water and steam pipelines shall be carried out in accordance with the Code for Construction and Acceptance of Industrial Metal Pipelines, GB 50235-1997.
5. For details of the construction method and the main node structure, see the National Building Standard Design Atlas of the table below.
02R110 "Atlas of Gas (Oil) Boiler Room Engineering Design and Construction"
02R111 "Atlas of Small and Horizontal Oil Tanks"
02R112 "Atlas of Tank Tops"
WNS 15t/h Best Service and Technical Support Industrial Gas Fired Steam Boiler
| ||Rated||Rated working||Rated steam||Suitable||Feed water|
|Model||output||pressure ||temperature ||fuel kind||temperature |
| ||(t/h)||(Mpa)|| (ºC)|| || (ºC)|
|WNS0.5-0.7/1.0/1.25-YQ||0.5||0.7/1.0/1.25||170/184/194||heavy oil/light oil,natural gas/lpg/city gas||20|
WNS15t / h Gas fired steam Boiler with stainless steel outer shell